GPRS 2G 4G high voltage smart circuit breaker 16A 32A 63AThe device integrates smart meter, reclosed circuit breaker, and wireless collector. It can realize high-precision metering of single-phase/three-phase AC power supply circuit and built-in power control of various smart logics.
- Protection function: Monitor the power consumption of the output terminal and automatically cut off the power supply if an abnormal situation occurs.
- Automatic coincidence: Realize automatic reclosing in an unattended environment after the line returns to normal.
- Metering function: With high-precision voltage and current real-time monitoring and energy metering, which will help to analyze the energy consumption of the electrical devices.
- Wireless communication: With local RS485 communication and GPRS (2G / 3G) wireless communication, it can realize remote opening and closing control, fault inquiry, and timing reporting of measurement data.
- Devices management: With perfect fault condition monitoring (overload, short circuit, over-voltage and under-voltage, phase loss, phase imbalance) and can report and give alarm prompts in real time.
- Electricity management: With a rate measurement in accordance with the national standard and can realize freezing data operation. Combined with wireless communication, remote management of electricity charges can be realized, and if arrears, the loop will close and all the devices will stop working.
- Humanized display interface: With an oversized LCD screen for remote and local information communication. The metering parameter and device status information is clear at a glance.
|Standard RS485 / NetworkGPRS-2G/3G+RS485
DL/T1487-2015, DL/T1485-2015, DL/T533-2007,
|short circuit, overload, over/under voltage, phase loss, alarm, remote
2500V/min Tripping time:<0.2S
TypeB, TypeC, TypeD
5A max(250VAC)resistor load
280/115V( default value, configurable in platform)
63/80A (default value, configurable in the platform)
|Trip≤0.3s, Reclose≤0.8s(exclude time delay)
|DIN installation of 35mm
-25°C~+65°C / -40°C~+75°C
|Identified the circuit fault, the electrician should pull out the safety lock and hang with a lock to solve the problem. Then, push back the safety lock, and try manually switching on the handle. If unsuccessful, electrician needs to check credit overdue or remotely switched off, by either RS485 or GPRS.
|It is under operation mode while safety lock not pulled out.
|It is under maintenance mode while safety lock is pulled out and needs to hang a lock. This safety lock has interlock with handle, and can't switch on, even manually, while lock pulled out. More security to maintenance electrician.
Company & Factory info:
Guangdong HonorInsight Iot Technology Co., Ltd. is a high-tech enterprise dedicated to the research and development of the key technologies of the Internet of Things and big data as well as the promotion of industrialization, and to improve the intelligence level of enterprises, institutions and cities. The company chooses "simple and trustworthy, open and win-win" as its purpose, and always helps the government and enterprises to achieve efficient information management and zero emissions.
At present, the company mainly provides smart city lighting management system based on Internet of Things like LoRa, NB-IoT and other communication technologies, photovoltaic power generation off-grid and grid-connected systems, environmental monitoring systems, smart city platforms, private cloud construction and other services.
With ahead hardware and software solutions, supply chain channel integration capabilities, data value development capabilities and complete vertical service genes, we focus on the four major segments of smart PV, smart community, smart site and smart agriculture, together bringing a group of professional background talents from Baidu, Huawei, Tencent, Jinli, Yangzhi, Cisco, etc. In product planning, big data analysis, hardware access, UI design, mobile development, cloud building, system integration, data products and applications.